Computerworld - Sal Azzaro, director of facilities for Time Warner Cable Inc., is trying to cram additional power into prime real estate at the company's 22 facilities in New York.
"Its gone wild," says Azzaro "Where we had 20-amp circuits before, we now have 60-amp circuits." And, he says, "there is a much greater need now for a higher level of redundancy and a higher level of fail-safe than ever before."
If Time Warner Cable's network loses power, not only do televisions go black, but businesses can't operate and customers can't communicate over the company's voice-over-IP and broadband connections.
When it comes to the power crunch, Time Warner Cable is in good company. In February, Jonathan Koomey, a staff scientist at Lawrence Berkeley National Laboratory and a consulting professor at Stanford University, published a study showing that in 2005, organizations worldwide spent $7.2 billion to provide their servers and associated cooling and auxiliary equipment with 120 billion kilowatt-hours of electricity. This was double the power used in 2001.
According to Koomey, the growth is occurring among volume servers (those that cost less than $25,000 per unit), with the aggregate power consumption of midrange ($25,000 to $500,000 per unit) and high-end (over $500,000) servers remaining relatively constant.
One way Time Warner Cable is working on this problem is by installing more modular power gear that scales as its needs grow. Oversized power supplies, power distribution units (PDU) and uninterruptible power supplies (UPS) tie up capital funds, are inefficient and generate excess heat. Time Warner Cable has started using Liebert Corp.'s new NX modular UPS system, which scales in 20-kilowatt increments, to replace some of its older units.
"The question was how to go forward and rebuild your infrastructures when you have a limited amount of space," Azzaro says.
With the NX units, instead of setting up two large UPSs, he set up five modules -- three live and the other two on hot standby. That way, any two of the five modules could fail or be shut down for service and the system would still operate at 100% load.
Some users are trying innovative approaches. One new way of approaching the power issue is a technique called combined heat and power, or cogeneration, which combines a generator with a specialized chiller that turns the exhausted waste heat into a source of chilled water. (See related story.)
Another new approach is to build data centers that operate off DC rather than AC power. In a typical data center, the UPSs convert the AC power coming from the utility's main power supply into DC power, then back into AC again. Then the server power supplies again convert the power to DC for use within the server.
- Hadoop for Dummies Today, organizations in every industry are being showered with imposing quantities of new information. Along with traditional sources, many more data channels and...
- The Top Five Ways to Get Started with Big Data Despite the increased focus on big data over the past few years, most organizations are still talking about what big data is rather...
- Data Warehouse Augmentation: The Queryable Data Store While organizations have, to date, been busy exploring and experimenting, they are now beginning to focus on using big data technologies to solve...
- The IBM Big Data Platform IBM is unique in having developed an enterprise class big data platform that allows you to address the full spectrum of big data...
- Live Webcast Best Practices: How to Improve Business Continuity with Virtualization VMware solutions include a range of business continuity capabilities to help ensure availability for applications across your virtualized environment. Learn More>>
- Endpoint Data Management: Protecting the Perimeter of the Internet of Things Not surprisingly, "Internet of Things" (IoT) and Big Data present new challenges AND opportunities for enterprise IT. Teams need to harness, secure and...
- Best Practices: How to Improve Business Continuity with Virtualization VMware solutions include a range of business continuity capabilities to help ensure availability for applications across your virtualized environment. Learn More>> All Data Center White Papers | Webcasts